Hazen-Williams Friction Loss Equation
Hazen-Williams friction loss calculator for water flow in pipes
Units: ft=foot, m=meter, s=second.
Hazen-Williams Equation: V = k C (D/4)0.63 S0.54 where S = hf / L and Q = V π D2 / 4
k is a unit conversion factor:
Hazen-Williams Coefficient (C) varies from approximately C=60 for 40-year old cast iron pipe to C=150 for new plastic pipe. The higher the C, the smoother the pipe. Table of Hazen-Williams Coefficients.
The Hazen-Williams method is valid for water flowing at ordinary temperatures of 40 to 75 oF (4 to 25 oC) through pressurized pipes. The Hazen-Williams equation is typically used to analyze city water supply systems. For other liquids or gases, the Darcy-Weisbach method should be used. Major loss (hf) is the energy (or head) loss (expressed in length units - think of it as energy per unit weight of fluid) due to friction between the moving fluid and the pipe wall. It is also known as friction loss. The Darcy-Weisbach method is generally considered more accurate than the Hazen-Williams method. However, the Hazen-Williams method is very popular, especially among civil engineers, since its friction coefficient (C) is not a function of velocity or pipe diameter. Hazen-Williams is simpler than Darcy-Weisbach for calculations where you are solving for flowrate (discharge), velocity, or diameter. More Discussion and References.
© 1998-2023 LMNO Engineering, Research, and
Software, Ltd. All rights reserved.
LMNO Engineering home page (more calculations)
Design of Circular Water Pipes Calculator (Hazen-Williams)
Circular Water Pipes with Pump Curve Calculator (Hazen-Williams)
Fire hydrant flow test analysis
Table of Hazen-Williams Coefficients (C)