PARSHALL FLUME Calculations, Equations, Graphs Based on ISO 9826 methodology 

To:
LMNO Engineering home page Weirs: Rectangular V Notch Cipoletti 
Register to fully enable "Calculate" button. Demonstration mode for 0.49 m < b < 0.51 m (b is flume throat width).
Links on this page: Equations Comments about graphs
Comparison of ASTM D1941 and ISO 9826 Variables
Units Error Messages
References
Introduction
Our Parshall flume calculation is based on the ISO 9826 (1992) standard. The
standard is valid for submerged as well as freeflowing Parshall flumes. A free flowing
flume can be identified by the drop in water depth at the flume throat. In submerged
flow, the downstream water backs up into the throat swallowing the drop making the drop
difficult or impossible to identify. Analysis of submerged flow requires two head
measurements  one in the approach channel and one in the throat. Whereas, free flow
requires only the upstream head measurement.
Parshall flumes must be built with their dimensions in strict accordance with specifications in published documents such as the ISO 9826 and ASTM D1941 (1991) standards or USBR (1997). Flumes (like weirs) are designed to force a transition from subcritical to supercritical flow. In the case of Parshall flumes, the transition is caused by designing flumes to have a narrowing at the throat and a drop in the channel bottom. Such a transition causes flow to pass through critical depth in the flume throat. At the critical depth, energy is minimized and there is a direct relationship between water depth and velocity (and flowrate). However, it is physically very difficult to measure critical depth in a flume because its exact location is difficult to determine and may vary with flowrate. Through mass conservation, the upstream depth is related to the critical depth. Therefore, flowrate can be determined by measuring the upstream depth, which is a highly reliable measurement. Like all of LMNO Engineering's software, our Parshall flume calculation was written in double precision.
Equations and Methodology
Back
to calculation
The methodology for our Parshall flume calculation follows that of ISO 9826 (1992).
ASTM D 1941 (1991) also addresses Parshall flumes but has pages of tabular data
which are more difficult to implement into a computer program compared to the figures and
equations of ISO 9826.
Variable definitions can be found in the Variables section.
Validity
LMNO Engineering calculation allows 0<=h<=3 m and 0.01<b<16 m, but the
calculation is most accurate when used within the ISO 9826 recommendations of h<=2
m and 0.152 <= b <= 15.24 m.
For b<=0.152 m, C and n values are from Herschy (1995). For b>0.152 m, C and n
values are from ISO 9826 (1992), equations 10 and 11.
Free flow
Free flow occurs when a hydraulic jump is visible at the throat; that is,
when the downstream head is significantly less than the upstream head. Our
calculation defines free flow as occurring when H/h<=0.6 for b<3.05 m or when
H/h<=0.8 for b>=3.05 m. These criteria (called "modular limits") are
similar, but not identical, to the ISO 9826 criteria.
For free flow,
Q = C h^{n} where Q is in m^{3}/s and h is in m
Submerged flow
Submerged flow occurs when a hydraulic jump is not visible at the throat;
that is, when the downstream head is sufficiently high that it "drowns out" or
"swallows up" the hydraulic jump. In our calculation, submerged flow
occurs when H/h>0.6 for b<3.05 m and when H/h>0.8 for b>=3.05 m.
For submerged flow, ISO equation 12 is rewritten as:
Q = C h^{n}  Q_{e} where C and n are found from the
above figure based on width (b). Q_{e} accounts for the effects of
submergence.
For b<3.05 m, ISO 9826 equation 13 provides the following equation for Q_{e} which is implemented in our calculation:
For b>=3.05 m, Q_{e}=C_{s}Q_{3}
C_{s} =(0.3281)b. ISO 9826 Figure 2 is a graph of Q_{3} as a
function of H/h and h. LMNO Engineering fit equations to all of the lines in
the ISO figure for use in our calculation. A graph using our equations for selected
H/h ratios is shown:
Comments about the Graphs
Back to calculation
When the graph "Q vs. H/h (h constant)" is selected, you may notice a
discontinuity in the graph at H/h=0.6 for b<3.05 m or H/h=0.8 for b>=3.05 m.
The discontinuity occurs because the flow is transitioning from free flow to submerged
flow. For some ranges of H/h, you may observe something similar to the following:
Graph of Q vs. H/h, for b=0.5 m and h=0.5 m
The discharge for H/h<0.6 does not appear to be shown. However, our software scales the yaxis based on the maximum value on the curve. In this case, the maximum value on the curve is 0.398 m^{3}/s which blends in with the boxed outline of the graph. The flow is 0.398 m^{3}/s for all H/h <0.6.
Comparison of ISO and ASTM methods
Back
to calculation
Both ISO 9826 and ASTM D1941 present methods for computing discharge through Parshall
flumes. Since a Parshall flume is a standard flume, the two methods should be
similar. Looking at the two standards, they at first appear somewhat different
because ISO 9826 is in SI units while ASTM D1941 uses predominantly English units.
Further, the ISO standard presents information in tables, equations, and figures while
ASTM D1941 uses tables almost exclusively. Curious as to how well the two methods
compare, we developed the following table. We also have done other comparisons but,
due to space considerations, have chosen not to show the results on this web page.
In general, there is good agreement for free flow, but in some cases the submerged
flowrates are significantly different, such as for the b=0.152 case shown below.
Comparison of ASTM D1941 and ISO 9826  
Width, b  Upstream Head, h  Flow Regime  ASTM Flow, Q  ISO Flow, Q 
0.152 m (6 inch) 
0.24 m (0.7874 ft) 
Free Flow  0.0400 m^{3}/s^{(1)}  0.0408 m^{3}/s^{(2)} 
Submerged, H/h=0.84  0.0309 m^{3}/s^{(3)}  0.0237 m^{3}/s^{(4)}  
7.62 m (25 ft) 
0.6096 m (2.0 ft) 
Free Flow  8.13 m^{3}/s^{(1)}  8.13 m^{3}/s^{(2)} 
Submerged, H/h=0.9  7.34 m^{3}/s^{(5)}  7.36 m^{3}/s^{(6)}  
^{(1)} based on Table 2 in ASTM D1941. ^{(2)}
based on Equation 10 in ISO 9826. ^{(3)} based on Tables 2 and 6B in ASTM D1941. ^{(4)} based on Equations 10, 12, and 13 in ISO 9826. ^{(5)} based on Tables 2, 9A, and 9C in ASTM D1941. ^{(6)} based on Equations 11, 12, and 14 and Figure 2 in ISO 9826. 
Variables
Back
to calculation
ISO 9826 specifies the indicated units for the equations shown above. Our
calculation allows you to specify a variety of units.
m=meters, s=seconds
b=Throat width [m].
C=Parshall flume constant [empirical units].
C_{s}=Submergence coefficient [unitless]. This is not the submergence
ratio.
h=Measured upstream head [m].
H=Measured downstream head [m]. Only needed if the flume is submerged, or to
determine mathematically if the flume is submerged. Usually, one can visually see if
there is a hydraulic jump, but determining the ratio H/h is a quantitative method.
H/h=Submergence ratio. Flume is submerged if H/h>0.6 for b<3.05m or if
H/h>0.8 for b>=3.05 m.
n=Parshall flume power constant [unitless].
Q=Flowrate (discharge) through flume [m^{3}/s].
Q_{e}=Reduction in flowrate due to submergence [m^{3}/s].
Q_{3}=Flow factor for determining Qe if b>=3.05 m [m^{3}/s].
Units
Back
to calculation
Most units are selfexplanatory. MGD is millions of gallons (US) per day.
Error Messages given by calculation
Back
to calculation
Input checks in top half of calculation. If one of these
messages appears, the calculation and graphing is halted.
"Must have h >= 0". Negative head was entered. If h=0,
calculation automatically sets Q=0.
"h must be < 3 m". Head cannot exceed 3 m.
"Must have H > 0". For submerged flow, downstream head must be
positive.
"Must have H/h > 0", "Must have H/h<0.99". If
submerged flow is selected, H/h must be in this range. However, if b<3.05 m and
H/h<=0.6, flow is considered to be free flow and will be computed using Q=C h^{n}.
Likewise, if b>=3.05 m and H/h<=0.8, flow is considered to be free flow.
"Must have b > 0". Throat width must be positive.
"Must have 0.01<b<16 m". Flume throat width must be in this
range.
Input checks for graph. If one of these messages
appears, the graph will not proceed. Note that if any value is out of range in the
upper portion of the calculation, a graph will not be shown.
"Min h must be >=0", "Min H/h must be >=0".
Minimum head or H/h ratio entered for graph cannot be < 0.
"Max h must be <= 3 m". Graph has maximum limit of h=3 m.
"Must have 0.6<Max H/h<=1". Message will only appear if
b<3.05 m. Q is independent of H/h until H/h becomes greater than 0.6. So to
avoid a "boring" graph showing a constant value for Q, the calculation requires
that max H/h be in the range where submergence affects Q.
"Must have 0.8<Max H/h<=1". Message will only appear if
b>=3.05 m. Q is independent of H/h until H/h becomes greater than 0.8. So
to avoid a "boring" graph showing a constant value for Q, the calculation
requires that max H/h be in the range where submergence affects Q.
"Min/Max must be < 0.99". Minimum value entered for graph must
be less than 0.99 times maximum value entered for graph. Otherwise, the minimum and
maximum are too close together to have good axis labels for the graph.
"Min must be < Max". Minimum value entered for graph must be
less than maximum value entered for graph.
Runtime errors. The following message may be generated
by the graphing portion of the calculation:
"No flow: H/h too low". Will occur if all of the flowrates for
the graph are 0.0. For example, if b=0.5 m, H/h=0.9, and a head range of 0 to 0.05 m
is entered for the graph, no water will flow through the flume since there is insufficient
head difference. All of the Q's will be 0.0, so the message is shown. For
these b and H/h values, h must be greater than 0.118 m before there will be flow.
References
Back to calculation
American Society for Testing and Materials (ASTM D194191). 1991. Standard
test method for open channel flow measurement of water with the Parshall flume.
Available at http://www.astm.org.
Herschy, Reginald W. 1995. Streamflow Measurement. E & FN Spon (an imprint of Chapman and Hall). 2ed.
International Organization of Standards (ISO 9826). 1992. Measurement of liquid flow in open channels  Parshall and SANIIRI flumes. Reference number: ISO 9826:1992(E). ISO documents can be downloaded as .PDF files for a fee at http://webstore.ansi.org.
USBR. 1997. U.S. Department of the Interior, Bureau of Reclamation. Water Measurement Manual. 1997. 3ed. Available from http://www.usbr.gov/pmts/hydraulics_lab/pubs/wmm/index.htm .
© 20012010 LMNO Engineering, Research, and Software, Ltd. (All Rights Reserved)
LMNO Engineering, Research, and Software, Ltd.
7860 Angel Ridge Rd. Athens, Ohio 45701 USA
(740) 5921890
LMNO@LMNOeng.com http://www.LMNOeng.com
(March 17, 2010: thickened graph line for better visibility)