Weymouth, Panhandle calculation is mobiledevicefriendly as of August 20, 2015
Register to enable "Calculate" button.
Units: acfd=actual cfd, acfh=actual cfh, acfm=actual cfm,
cfd=cubic foot per day, cfh=cubic foot per hour, cfm=cubic foot per minute, cfs=cubic foot
per second, cm=centimeter, hr=hour, kg=kilogram, km=kilometer, lb=pound, m=meter,
mm=millimeter, Mcfh=thousand cfh, MMcfd=million cfd, N/m^{2}=Newton per square
meter (same as Pascal), s=second, psi=pound per square inch, psia=psi (absolute), psig=psi
(gage), scfd=std cfd, scfh=std cfh, scfm=std cfm, std=standard conditions (60F, 14.7
psia).
Introduction
The Weymouth, Panhandle A, and Panhandle B equations were developed to simulate
compressible gas flow in long pipelines. The Weymouth is the oldest and most common
of the three. It was developed in 1912. The Panhandle A was developed in the 1940s and
Panhandle B in 1956 (GPSA, 1998). The equations were developed from the fundamental energy
equation for compressible flow, but each has a special representation of the friction
factor to allow the equations to be solved analytically. The Weymouth equation is the most
common of the three  probably because it has been around the longest. The equations were
developed for turbulent flow in long pipelines. For low flows, low pressures, or short
pipes, they may not be applicable.
If the pressure drop in a pipeline is less than 40% of P_{1}, then our DarcyWeisbach incompressible flow calculation may be more
accurate than the Weymouth or Panhandles for a short pipe or low flow. The
DarcyWeisbach incompressible method is valid for any flow rate, diameter, and pipe length,
but does not account for gas compressibility. Crane (1988) states that if the
pressure drop is less than 10% of P_{1} and you use an incompressible model, then
the gas density should be based on either the upstream or the downstream conditions.
If the pressure drop is between 10% and 40%, then the density used in an incompressible
flow method should be based on the average of the upstream and downstream
conditions. If the pressure drop exceeds 40% of P_{1}, then use a
compressible model, like the Weymouth, Panhandle A, or Panhandle B. You can always
run all models and compare the results. The calculation is only valid for subsonic velocities. It does not check
if velocities are sonic or supersonic.
Equations
The equations are shown below. The Weymouth, Panhandle A, and Panhandle B equations (GPSA,
1998; Crane, 1988) are the equation beginning with Q_{s}=... with the
constants c, n, u, x, and y defined below. All of the equations shown below use the
English units indicated in the Variables section. Of course, our calculation uses a
variety of units with all of the unit conversions handled internally by the program.
Variables:
The units refer to the units that must be used in the equations shown above.
However, a variety of units may be used in our calculation.
A = Pipeline crosssectional area.
c = Constant. Weymouth: c=18.0625, Panhandle A: c=18.16125, Panhandle B: c=30.7083
D = Pipe inside diameter [inch].
E = Efficiency factor. Typically 0.85 to 1.0. The lower the number, the
rougher (or older) the pipe. Typical value is 0.92.
L = Pipeline length between locations 1 and 2 [mile].
n = Constant. Weymouth: n=2.6667, Panhandle A: n=2.6182, Panhandle B:
n=2.53
P = Absolute pressure in pipeline [psia, i.e. pounds per square inch absolute].
Q = Volumetric flowrate [cfh, i.e. cubic foot per hour]
S = Specific gravity of gas in pipeline, relative to air. That is, the ratio of the
gas's molecular weight to the molecular weight of air [unitless].
T = Absolute temperature [Rankine]. Note: ^{o}R=^{o}F+459.67
u = Constant. Weymouth: u=1.0, Panhandle A: u=1.0788, Panhandle B:
u=1.02
V = Velocity of gas = Q/A.
W = Mass flowrate [lb/hr, i.e. pounds per hour].
x = Constant. Weymouth: x=1.0, Panhandle A: x=0.853, Panhandle B: x=0.961
y = Constant. Weymouth: x=0.5, Panhandle A: x=0.5392, Panhandle B: x=0.51
Z = Gas compressibility. Value typically 1.0 at standard conditions. Typically
decreases as pressure increases. Can be as low as 0.4 or so. Exact computation
depends on makeup of the gas, gas critical pressure and temperature, and actual
temperature and pressure.
ρ = Greek letter rho. Density [lb/ft^{3}, i.e. pounds per cubic
foot]. Note that the equation for ρ_{s} uses a value of 1.0 for the
compressibility.
Subscripts:
1 = Upstream conditions.
2 = Downstream conditions.
atm = Atmospheric conditions (14.73 psia).
s = Standard conditions (520 R, 14.73 psia)
Error Messages given by calculation
"Need D>0", "Need L>0", "Need S>0", "Need
Q_{s}>0", "Need W>0", "Need E,Z > 0".
These are initial checks. Diameter, length, specific gravity, and flows must be positive
numbers.
"Need T>0 K", "Need P_{1}>0 absolute", "Need
P_{2}>0 absolute", "Need P_{1}>P_{2}".
Temperature must be greater than absolute zero. Pressures must be greater than 0 absolute.
And, pressure difference must be positive. Since you may have entered temperature in other
units or pressure as gage, the calculation does some initial computations to determine the
validity of the input.
"P_{1} too small". This message appears if P_{2}
is computed as less than 0 absolute.
References
Crane Co. 1988. Flow of Fluids through Valves, Fittings, and Pipe.
Technical Paper 40 (TP40). http://www.craneco.com
GPSA (Gas Processors Suppliers Association). Engineering Data Book. 11ed.
1998. https://gpsa.gpaglobal.org
© 20032015 LMNO Engineering, Research, and
Software, Ltd. All rights reserved.
Please contact us for consulting or other questions.
LMNO Engineering, Research, and Software, Ltd.
7860 Angel Ridge Rd. Athens, Ohio 45701 USA Phone and
fax: (740) 5921890
LMNO@LMNOeng.com http://www.LMNOeng.com

To:
LMNO Engineering home page (more calculations)
Related Calculations:
DarcyWeisbach incompressible flow calculator
Choked gas flow
Gas flow conversions (mass, standard, actual)
Unit Conversions
Trouble printing?
Register
